You cannot log in without being assigned a valid TSI role.
Controlling the spread of airborne infectious disease can be challenging for hospitals and other healthcare facilities. Groups such as the Facilities Guidelines Institute (FGI), US Centers for Disease Control (CDC), American Society of Healthcare Engineers (ASHE) have written standards such as ASHRAE 170-2017 requiring positive room pressure and negative room pressure differentials for specific rooms. Airborne infectious isolation (AII) rooms require negative room pressure to contain airborne bacteria in the room. Operating rooms and protective environment (PE) rooms require positive room pressure to keep pathogens out.
Designing a hospital for positive room pressure or negative room pressure differentials is not enough. Room pressure differential must be monitored to ensure occupant health and to comply with standards. Two technologies are used to measure room pressure differential: capacitive pressure transducers and through-the-wall (TTW) pressure sensors.
Hospitals traditionally use capacitive pressure transducers to measure room pressure differentials. This method uses plastic tubing installed in the walls to send the pressure from the rooms to the pressure transducer. The room pressure differential changes the capacitance between two membranes inside the pressure transducer. The pressure transducer determines the pressure differential by measuring this capacitance. Capacitive pressure transducers are best for measuring pressure transducers much larger than hospitals use for AII, PE and operating rooms. Temperature changes can affect the accuracy of capacitive pressure transducers. Capacitive pressure transducers are also vulnerable to drift, leading to false alarms if they are not frequently recalibrated.
TTW pressure sensors use thermal anemometry to measure air velocity and direction through a small opening in the wall. TTW sensors convert the air velocity to pressure differential, just like pitot tubes are often used to measure air velocity by measuring air pressure. TTW pressure sensors are the most accurate way to measure room pressure differential. Most importantly, they are proven to be stable so the room pressure measurement does not need frequent calibration to remain accurate.
Meet PresSura Monitors & Controls
Watch this video featuring an introduction to PresSura™ Room Pressure Monitors and Controllers—offering the most accurate, precise, and stable measurement available. If you’re ready for isolation room development or expansion in your facility, contact TSI. We’re ready to help.
Read the latest news about TSI and industries we serve.
View All News
We are at the industry events important to you.
View all Events
We encourage curiosity and critical thinking. Browse TSI jobs.
Explore TSI Careers
TSI researchers and engineers hold more than 50 patents.
Browse TSI's Patents